What should we pay attention to when connecting Shanterups power supply to generatorIf Shanterups power supply is connected to the generator, the following steps should be taken:
Start the generator, after its stable operation, connect the generator's output power to UPS, the input end (at this time to determine that UPS is no load), then start UPS according to the boot-up procedure, after UPS is started, then connect the load one by one (it is recommended to select the generator capacity with twice the capacity of UPS).
Maintenance and maintenance
Batteries of standard models are valve-regulated, low maintenance, and need to be charged regularly to achieve life expectancy. UPS always charges batteries, whether on or off, and provides over-charge and over-discharge protection when connected to the same city.
If UPS is not used for a long time, it is recommended to charge it every four to six months.
Normally, the service life of the battery is three to five years. If the battery is found to be in poor condition, it must be replaced earlier. The replacement of batteries must be performed by professionals.
Batteries should not be replaced individually. Battery suppliers'instructions should be followed when replacing the battery as a whole.
Normally, the battery is charged and discharged every four to six months, and charged until the power off, and the charging time of the standard machine should not be less than 12 hours.
In high temperature areas, batteries are charged and discharged every two months, and standard machines are charged for no less than 12 hours each time.
As an uninterrupted protection power supply, Shante UPS power supply not only protects computer IT equipment or information data, but also has a wide application in construction hoist. It can be said that the power supply is necessary for our life and has brought us great convenience.