Santak UPS uninterrupted power supply proper maintenance and maintenanceBatteries of standard models are valve-regulated, low maintenance, and need to be charged regularly to achieve life expectancy. UPS always charges batteries, whether on or off, and provides over-charge and over-discharge protection when connected to the same city.
If UPS is not used for a long time, it is recommended to charge every four to six months.
Normally, the service life of the battery is three to five years. If the battery is found to be in poor condition, it must be replaced earlier. When battery is changed, it must be carried out by professional personnel.
Batteries should not be replaced individually. Instructions for battery suppliers should be followed when replacing them as a whole.
Normally, the battery is charged and discharged every four to six months, and charged until the power off, and the charging time of the standard machine should not be less than 12 hours.
In high temperature areas, batteries are charged and discharged every two months, and standard machines are charged for no less than 12 hours each time.