What does the CASTLE series fault code of Shanterups power supply mean?Hello, everyone, Xiaobian here to tell you about the common Shante UPS power failure code:
When the (+-) symbol at the bottom of Shanterups mainframe lights up the Yellow light, the battery discharge time is short and the battery is aging: change the battery in time
Shante UPS Power Overload: Check Load Level and Remove Important Load
Ensure that UPS is not overloaded, vent is not blocked and indoor temperature is not too high. Wait 10 minutes for UPS to cool down and restart. If it fails, please contact the manufacturer.
Turn off UPS, remove all loads, and confirm that there is no fault or internal short circuit. Reboot, if failed, please contact the manufacturer
1 # Failure Indicator and 4 # Light on, UPS Long Whistle: UPS Closed due to Internal Failure
Please contact the manufacturer.
1# Failure Indicator and 3# Lamp on, UPS Long Voice: UPS Overcharge Protection Action
Shante UPS charger malfunction, please contact the manufacturer
City Electricity Indicator Flash: City Electricity Voltage or Frequency Out of Shante UPS Power Supply Input Range (UPS calls twice a second, even eight tones at boot time)
At this time, Shante UPS is working in battery mode, saving data and shutting down the application to ensure that the power supply is in the input voltage or frequency range allowed by UPS.
Shunt UPS power supply is called two minutes a time: reconnect to make the Zero Fire Wire of Municipal Electricity connect correctly
1 # Fault Indicator and 2 # Light on, Shante UPS Power Sound: Battery Mode UPS or Load Equipment Fault Overload
Check load levels and remove non-critical devices, recalculate load power and reduce the number of loads connected to UPS to check if load devices are malfunctioning
Battery lamp flickers, battery voltage is too low or not connected to the battery: Check Shante UPS battery part, connect the battery well, if the battery is damaged, please replace the battery in time.